TR-1 Standpipe Systems (BC 1704.22)
1704.22 Standpipe system special inspection. New and altered standpipe systems shall be inspected in accordance with Section Sections 905 and 1704.22.1. The permit holder responsible for the standpipe work shall perform all required acceptance tests, and complete and sign the appropriate contractor's material and test certifications. The special inspector shall witness all required tests, verify that installation of all materials, fittings, hangers, assemblies and signage are in accordance with the approved construction documents, that painting of the standpipe system required by Section 905.11 of this code has been performed and that the contractor has transmitted required maintenance literature and instruction to the owner. The special inspector shall verify that the material and test certification forms have been transmitted to the Fire Department and the Department of Buildings‡.
Exception: Special inspection of The special inspector need not witness the hydrostatic pressure test shall not be required when such test is witnessed by the department.
DetailsSIGN-ON / Inspect / SIGN-OFF (package)